Fire pumps; have different features used for daily needs. We can enumerate the objective of fire pumps and materials required in fire pumps as follows:
- 1 electric motor pump, diesel engine spare pump with same capacity, in place of diesel-engine pump; 3 extra pumps that serve to back up half of the capacity are also selected. At the same time, it is necessary to keep 1 more pump due to leakage probability. If there is a generator capable of operating the pumps used for fighting against the fire; the spare pump can also be selected as electric motor just like the main pump.
- Zero flow pressure of the pump should not be more than 140% of the nominal pressure. If the capacity needed to fight against the fire is 200m3/h and 100 mss; the closed valve in the selected pump must not exceed 280 mss and fire pump curve must be parallel to the horizontal axis as much as possible.
- The pump selection should be done in such a manner that will operate at 1.5 times of the nominal flow. At the same time, the pump pressure should also not be lower than 65% of nominal pressure.
- 5-line soft gasket must be used for sealing. The reason for this; gaskets are able to continue to operate owing to their soft structure even though they’re damaged.
- A separate control board is also required for each pump in the pumps used for fire fighting.
In the group of pumps used for firefighting; there are fire pumps consisting of electric motor and diesel driven 2 main pumps and 1 extra jokey pump and fire pumps consisting of more than one electric motors driven pump and 1 extra pump.
Different operation system is available for the system in both 2 fire pumps and therefore the following elements may also be needed:
- Electric motor driven main pump system,
- Diesel engine driven main pump system,
- Electric motor driven 1 extra pump system,
- Pump control boards selected and applied for main pumps,
- Audible and lighted alarm devices.
- Instruments required to be integrated into buildings.
Yangın Pompası Fiyatları
Yangınla mücadelede kullanılan pompa gruplarında; birden çok elektrik motor tahrikli pompa ve 1 adet ekstra pompadan oluşan yangın pompaları ve elektrik motorlu ve dizel tahrikli 2 ana pompadan ve 1 adet ekstra jokey görevi gören pompadan oluşan yangın pompaları yer almaktadır.
Her 2 yangın pompalarında da sistemin değişik çalışma sistemi mevcuttur ve bu yüzden aşağıdaki elemanlara da ihtiyaç duyulabilmektedir:
Elektrik motoru tahrikli ana pompa sistemi,
Dizel motor tahrikli ana pompa sistemi,
Elektrik motoru tahrikli 1 adet ekstra pompa sistemi,
Ana pompalar için seçilen ve uygulanan pompa kontrol panoları,
Sesli ve ışıklı alarm cihazları,
Binalara entegre edebilmek için gerekli olan cihazlar.